1" Dry Horizontal Sidewall Sprinklers - Standard Response | Series GL-SR/DRY/HSW Glass Bulb - 5.6 K-factor
Not all temperatures and configurations may carry all Listings and Approvals. See data sheet for conditions of specific Listings and Approvals.
|temperature||135, 155, 175, 200, 286|
|approvals||cULus, FM, NYC|
STANDARD RESPONSE AUTOMATIC SPRINKLERS GL SERIES DRY TYPE HORIZONTAL SIDEWALLGFS 520b 20170406CM (.pdf) Download
|Horizontal Sidewall Revit Files (.zip)||Download|
|Sprinkler Globe Recessed Horizontal Sidewall GL Commercial QR Imp (.rfa)||Download|
|Sprinkler Globe Recessed Horizontal Sidewall GL Commercial QR Metric (.rfa)||Download|
Glass Bulb – 5.6 and 8.0K-factor Horizontal Dry Sidewall Sprinklers. Standard Response, Standard Coverage, Dry: Where standard response, standard coverage horizontal dry type sprinklers are specified to be utilized in freezing applications they shall be of an all bronze frame construction with brass deflector, with outer galvanized steel pipe and stainless steel inner tube construction. Sprinklers shall have a 5mm glass bulb thermally sensitive operating element, and rated for a working pressure of 175 psi. Sprinklers installed in areas without a finished ceiling shall be of a bronze/brass finish and shall be of an appropriate temperature classification for the hazard. Sprinklers installed under a finished ceiling shall be a chrome/white polyester finish. Sprinklers shall be UL listed or FM approved. Standard response, standard coverage, dry type horizontal sidewall sprinklers shall be of the Series GL-SR/DRY/HSW; as manufactured by Globe Fire Sprinkler Corporation.
WARNING: Cancer and Reproductive Harm – www.P65Warnings.ca.gov.