3/4" Conventional Sprinkler, Quick Response | Series GL-QR/CNV Glass Bulb - 8.0 K-factor
Not all temperatures and configurations may carry all Listings and Approvals. See data sheet for conditions of specific Listings and Approvals.
|temperature||135, 155, 175, 200, 286|
SERIES GL-QR/CNV STANDARD COVERAGE, QUICK RESPONSE CONVENTIONAL (OLD STYLE) SPRINKLER K-FACTOR: 5.6, 8.0GFS-101_20190916CM (.pdf) Download
|Sprinkler Globe Conventional GL Commercial QR Imp (.rfa)||Download|
|Sprinkler Globe Conventional GL Commercial QR Metric (.rfa)||Download|
Glass Bulb - 5.6 and 8.0 K-factor Conventional / Old Style Sprinklers. Quick Response, Standard Coverage: Where quick response, standard coverage conventional / old-style sprinklers are specified they shall be of an all bronze frame construction with brass deflector. Sprinklers shall have a 3mm fast response glass bulb thermally sensitive operating element, and rated for a working pressure of 175 psi. Sprinklers installed in areas without a finished ceiling shall be of a bronze/ brass finish and shall be of an appropriate temperature classification for the hazard. Sprinklers shall be LPC or CE approved. Quick response, standard coverage sprinklers shall be of the GL-QR/CNV Series; as manufactured by Globe Fire Sprinkler Corporation.
WARNING: Cancer and Reproductive Harm – www.P65Warnings.ca.gov.