3/4" Sidewall Sprinklers - Extended Coverage Quick Response | Series GL-QR/ECLH/SW Glass Bulb - 8.0 K-factor
Not all temperatures and configurations may carry all Listings and Approvals. See data sheet for conditions of specific Listings and Approvals.
|temperature||135, 155, 175, 200|
EXTENDED COVERAGE LIGHT HAZARD AUTOMATIC SPRINKLERS GL SERIES HORIZONTAL SIDEWALLGFS-225_20190315CM (.pdf) Download
|Horizontal Sidewall Revit Files (.zip)||Download|
|Sprinkler Globe Horizontal Sidewall GL ECLH Imp (.rfa)||Download|
|Sprinkler Globe Horizontal Sidewall GL ECLH Metric (.rfa)||Download|
|Sprinkler Globe Recessed Horizontal Sidewall GL ECLH Imp (.rfa)||Download|
|Sprinkler Globe Recessed Horizontal Sidewall GL ECLH Metric (.rfa)||Download|
Glass Bulb – 5.6 and 8.0 K-factor Sidewall, and Recessed Sidewall Sprinklers. Quick Response, Extended Coverage: Where quick response, extended coverage light hazard sidewall sprinklers are specified they shall be of an all bronze frame construction with brass deflector. Sprinklers shall have a 3mm glass bulb thermally sensitive operating element, and rated for a working pressure of 175 psi. Sprinklers installed in areas without a finished ceiling shall be of a bronze/brass finish and shall be of an appropriate temperature classification for the hazard. Sprinklers installed under a finished ceiling shall be a sidewall style sprinkler with an adjustable recessed escutcheon of the same specified finish. Sprinklers shall be UL listed. Quick response, extended coverage light hazard sidewall sprinklers shall be of the Series GL-QR/ECLH/SW; as manufactured by Globe Fire Sprinkler Corporation.
WARNING: Cancer and Reproductive Harm – www.P65Warnings.ca.gov.